Location: Perth, Australia
> Multiplex required a water treatment system to treat and dewater constructions sites – 400Kl/day capacity
> Supplied, installed and commissioned filtration system for a multiplex site
> Scope was to treat the water to Australian Drinking Water Guidelines and discharge into the Swan River.
> The raw water was a combination of ground water and accumulated rain water.
> The ground water was high in heavy metals including Iron (above 50mg/L) and aluminium (above 26mg/L).
> The project was supervised and monitored by the Swan River Trust (a State government agency charged with protecting and managing the Swan Canning river system).
> The treatment unit successfully produced water that met the Australian Drinking Water Guidelines.